How to indicate battery trouble of the V series on the PLC side
The condition of the V series battery is output to system device memory $s167.
For information about $s167, click here.
The condition can be transferred to the PLC as described below.
- Select [Home] -> [Registration Item] -> [Macro Block], specify an available number, and click [OK].
The [Macro Block] window is displayed.
- Use the MOV macro command, and create a macro to transfer data from $s167 to the PLC memory. When created, click [x] to close.
Example: Transfer data from $s167 to D100 in the PLC device memory.
- Select [System Setting] → [Macro Setting] → [Event Timer Macro] and check a number (not in use) under [Event Timer].
Set [Cycle Time] and the macro block number created in step (2), and click [OK].
Example: Execute macro block No. 0 every 300 seconds (5 minutes).
Data in $s167 will be transferred to D100 in the PLC device memory.
Was this page helpful?
Please cooperate with the questionnaire to make it better.